Best A/C and Heating Services in Fort Worth
Fort Worth summers can be unbearable when you don’t have reliable air conditioning at your home or business. Even in winter, not having dependable heat can make your place feel much colder than it should. Whether you need repairs done on your heating system or air conditioning system, Comfort Masters can help. We also don’t want you to have to deal with an HVAC system that is on its last leg, so we offer high-quality installation services, which include helping you choose the most suitable and efficient system for your property.
At Comfort Masters Heating & Air Conditioning, we’re committed to providing residential and commercial customers in Fort Worth with prompt service that they can depend on. Whether you want to set up regular maintenance, have repairs done, or get a new HVAC system, you can turn to us for help. Keep in mind that we also offer air duct maintenance, installations, and repairs to help you maintain clean air and a comfortable temperature at your home or business.
A/C and Heating Unit Installation and Repair in Fort Worth
When your furnace breaks down or you need a brand new A/C unit, our team of licensed HVAC professionals will be there for you. Comfort Masters offers A/C and heating unit installation and repair in the Fort Worth area. We have technicians available who can work with electric furnaces, heat pumps, gas furnaces, and other types of HVAC equipment to ensure that it’s repaired or installed correctly.
Running your air conditioning in summer and your heat in winter take a toll on your HVAC equipment. When the time comes for you to replace old or worn out HVAC equipment, you can count on us to handle it for you.
Comfort Masters’ Commitment to Great Customer Service
When you hire an HVAC company, you don’t always know what quality of service you’ll end up getting. You don’t have to worry about that when you rely on Comfort Masters for your HVAC service. Since 2003, we have built a solid reputation for providing excellent service to our customers in Fort Worth. Company managers Stephen P. Moore and Jesse I. Roberts, as well as our team of highly trained and knowledgeable technicians, have remained dedicated to providing every customer with the highest quality service.
You don’t have to look far to find evidence of our customer service quality. Customers who have hired us in the past have posted online reviews that praise on our technicians for being able to show up on time or even a bit earlier than expected. Our customers also appreciate being able to depend on having HVAC work done with expert care. Our company has been awarded for Superior Service by Angie’s List, and the Better Business Bureau has also given us an A+ rating.
Living in Fort Worth
Fort Worth is a thriving city that offers housing that is lower than average compared to the rest of the state and the U.S. overall. Home prices in Fort Worth are around $131,100 on average, while average home prices in Texas are around $142,700 and around $184,700 in the U.S. The median household income in Fort Worth is $54,876, which is on par with the state average of $54,727 and the national average of $55,322.
There are around 874,168 people who make their home in Fort Worth thanks to great employment opportunities, good schools, and a wide range of amenities and activities. The city is also close to other towns and cities in the greater DFW area. Dallas is about 32 miles away via I-30 E, while Arlington is around 15 miles away via I-30 E. Irving is about 26 miles away via TX-121 N and TX-183 E.
Residents in Fort Worth have plenty of local attractions and amenities to enjoy, no matter what their interests are. Take the whole family to the Fort Worth Zoo to see more than 7,000 animals, or spend the day at the Fort Worth Museum of Science and History. Other notable attractions include the Fort Worth Japanese Garden, Fort Worth Nature Center and Refuge, and the Stockyards National Historic District.
Fort Worth residents who are interested in volunteering their time and skills can help out in a number of ways. Some of these opportunities include Animal Care and Control, Keep Fort Worth Beautiful, Fort Worth Park and Recreation Department, and Citizens Police Academy. The city also has several Boards and Commissions available to join, such as the Art Commission, Aviation Advisory Board, Downtown Design Review Board, and Library Advisory Board.
If you’re a homeowner or business owner in Fort Worth and you need high-quality HVAC services for your property, contact Comfort Masters Heating & Air Conditioning. Our HVAC experts can install, repair, or maintain your HVAC system to help your home or business feel comfortable throughout the year.
for Fort Worth, TX
Chris - Fort Worth, TX
Friendly and fast service
Anthony - Fort Worth, TX
Great technician. Friendly, professional and timely service.
Tony - Fort Worth, TX
Bobby came out and got right to work. Found the leak on our mini-split and repaired quickly. Thanks!!
Sue - Fort Worth, TX
We call Comfort Masters because of fast, honest, and professional service. James didn’t disappoint.
Very helpful and insightful service!
Chance - Fort Worth, TX
Bobby was extremely helpful and prompt. He also educated me on best practices and was definitely looking out for my best interest.
Rick - Fort Worth, TX
James did an awesome job. Was very friendly and forthright with what needed to be done to the unit. Will definitely use Comfort Masters again. I didn’t give cost a rating, due to I didn’t get another opinion or see how much the motor would’ve cost me solo.
Bobby was great!
David - Fort Worth, TX
Bobby was our technician and he was great. He spent time making sure I understood how the dampers work and also made sure our system was setup correctly even though at first glance it didn’t seem to be.
Super Awesome Service
Kristen - Fort Worth, TX
Came home Monday night to air blowing but it wasn't cooling. Called Comfort Masters Tuesday morning at 0800 and Bobby was at my house that afternoon. He did a thorough inspection of unit and diagnosed the problem. He explained all my options, was extremely transparent about what he would be doing and made sure I was comfortable with everything he was going to do. He explained the maintenance options but was very low pressure on purchasing one. I would highly recommend Comfort Masters for any heating and cooling needs you may have.
Jon - Fort Worth, TX
Very happy with Gino's work and knowledge of the system! He did an excellent job! $254 for a $10-20 capacitor, even with simple swap labor, was way too expensive - I felt overly ripped off.
Amazing customer service
April j. - Fort Worth, TX
called comfort matters for a service inspection. BOBBY arrived and figured out what maintenance issues we were having, right away! Bobby you are very Friendly, informative and, very knowledgeable . I appreciate your thorough explanations and the time you took in making sure that you checked every thing off your list. Thanks for installing the air scrubber! We signed up for regular maintenance after Bobby explained how important maintenance is to our system.Thanks!
9-23-2020, Arrived on site and discussed options of club membership versus one time maintenance with the customer. Went ahead and performed maintenance on the heat side. Checked and verified heat strips are working properly with 61.2A, emergency heat temperature split 30°, heat pump temperature split 93°, replaced 20 x 25 x 4 filter that customer supplied. Variable speed blower motor at 2.33 A, due to weather the pressures are going to be off. No float switch in primary drain line is clogged. Recommend unclogging and adding a float switch with drain pan tablets to help reduce the potential of future drain clogs. Found dual capacitor is extremely weak and needs to be replaced before compressor fails. Verified reversing valve working properly, defrost sensor working. When ahead and sign customer up with the standard club membership and performed the repairs of Installing float switch with pan tablets and clearing out drain line with nitrogen and water with chemicals. Also replaced dual c
9-22-2020, was asked to look at the right side unit due to it not cooling properly. Larry also asked if I can look at the left side unit. I advised him due to the weather I will do my best. While inspecting the right side unit I found extreme rust on the emergency drain pan and open the evaporator coal to verify all the residue and rusting on the evaporator coil. I performed a basic leak search and found a leak on the bottom left corner. I took a video for our records. While I had my leak detector in the attic, I went ahead and performed a basic leak search on the second unit due to seen large amounts of rust debris and oxidation on the second emergency pan as well. Unfortunately I found a leak on the second unit evaporator coal in multiple places. Larry has an appointment scheduled with Don to discuss options of replacement for either both systems or just the right side for now. Appointment scheduled for tomorrow with Don between 9 to 11 AM. Both units are 9 1/2 years old and both 3to
Preformed fall tune up!
Came out to perform quality check on client brand new up-flow gas heat Amana system, upon arrival spoke with client and she showed concerns that it seem to be cooler in a couple spots of the home. Went thru QC by checking wiring, settings, surge protectors, drain line, float switch, filter, overall cleanliness of install, overall seal of system, refrigerant charge, etc., etc.. while performing QC found a couple spots in the mastic seal that was a little thin and starting to crack, went ahead and sealed again with mastic to ensure proper seal for years to come. Also went into attic to see if there were manual dampers at start collars and was not able to find any. However after speaking to client again, I would recommend curve blade grilles in the living area so that we can divert air up and to ceiling fan, instead of them blowing directly on people who are sitting on the furniture. System is operating well within manufacturer specifications and install is very nice and clean. See pictur
Came out to perform prepaid maintenance on clients 1yr old system, upon arrival performed maintenance by checking motors, voltages, amperages, filter, drain line, float switch, delta t, capacitor, contactor, refrigerant charge, washed out the outdoor unit with water hose, etc., etc.. System is operating well within manufacturer specifications, please see checklist for details. Also spoke with client about Aexus Air Scrubber air purification system and client has chosen to decline at this time.
Replaced warranty furnace control board on Lennox gas up flow furnace. Signed up on standard membership.
Came out due to clients mini split system is leaking oil, upon arrival pulled air handler off the wall and perform leak search on line set where I found leak at suction line flare fitting, added sealant provided by manufacturer put back together, added 7 oz 410a refrigerant, leak searched it again and the leak has gone away. Added the remaining 2lbs 410a refrigerant started up system in the cool mode, system is operating with a 20° delta T with the return air temperature being 82° and the supply air temperature being 62°. System is operating per manufacture specifications.
Came out due to upstairs system is not cooling, upon arrival spoke with client and he stated that home warranty company came out and wanted to be paid before he even performed diagnostic, and then tech only spent a couple minutes on diagnostic and then left. Upon arrival to outdoor unit found that there was no high voltage to unit, found tripped breaker, checked compressor to ground and that compressor windings are gone to ground on the common and start windings. Unplugged compressor and tested operation of condenser fan motor, spoke with client about different options and client has chosen to have a comfort specialist come out today between 4-5pm. Went ahead and finished checklist by checking out the indoor unit please see checklist for detail. System is non operational at this time. If client does choose to go with new system today’s total will need to be credited to install.
Came out to perform inspection on duct work due to client has 2 vents that he believes are not getting enough air. Upon arrival walked home with client to get an idea of where the good and bad air flows, found that units return air grilles equal to 360sqin and because system is 3.5 ton actual return air space needed is 700sqin, can add an 8x30 grille in bedroom off of closet this will add 240 sq in for a total of 600. Then climbed in attic traveled across attic to plenum and found that someone has installed a nine inch duct to the top of the plenum, duct work has a lot of air leakage, and insulation is falling off of metal duct in a lot of places. Please see estimate. Spoke with client about our maintenance membership programs and client has chosen to with silver maintenance membership. Performed maintenance by checking motors, voltages, capacitors, filter, drain line, delta t, duct work, contactor, washed out the outdoor unit with water hose, etc., etc.. while performing maintenance f
Installing new 5 ton 16 seer condenser and coil.
Installed blower motor
Came out due to master suite unit not cooling, upon arrival performed service checklist by checking motors, voltages, amperages, drain line, duct work, filter, capacitor, contactor, refrigerant charge, etc., etc.. while performing checklist found that the fuse in the air handler was blown, pulled fuse and then installed reset-able fuse, tested operation in fan mode and cooling was not able to make fuse blow again. Replaced fuse and then performed checklist. Found that system is operating per manufacturer specifications, please see checklist for details. Client expressed concern that one of the bedrooms on the master suite unit stayed cooler than the rest, showed client manual dampers, explained how they work, and show him the different position and what those positions would do to the airflow. Notice that clients air scrubbers were unplugged, spoke with client in regards to this and he stated that the smell makes his wife sick, explained to client that air scrubber does offer a bulb th
8-27-2020, Per customers request I performed a one time summer maintenance on one system. Found system was slightly low on Freon and customer opt out at this time. Also customer was not interested in signing up for a membership or system enhancements today. Advised him that his system is a heat pump and will also need Freon during the winter. System does have a 19° temperature split across the coil. No other issues with the system found at this time. Return system back to normal use. Thank you
8-26-2020, Arrive today to perform a quality inspection on the upstairs unit that we recently installed. Verified everything is connected properly, wires are tight, Gas line is secure. All major components functioning properly. System is sealed properly. Drain line is clear, float switch is working. Great job on the install guys! Thank you
Came out due to system is not cooling, upon arrival performed checklist by checking motors, voltages, amperages, filter, drain line, float switch, delta t, capacitors, contactor, refrigerant charge, etc., etc.. while performing checklist found that compressor capacitor was reading 0 of 70mfd, and that condenser fan motor capacitor was reading 6.4 of 7.5mfd which is below manufacturer specifications, went ahead and replaced both capacitors with one 70/7.5 dual capacitor. Also found that the condenser coil was pretty dirty and causing high head pressure on system, spoke with client about our maintenance membership programs and client has chosen to go with our silver maintenance membership. Went ahead and washed out condenser coil thoroughly to ensure efficiency as well as longevity of life of the system. System is operating per manufacturer specifications, please see checklist for details.