Contact Comfort Masters Heating & Air Conditioning in Joshua, Texas
Hours of Operation:
Open 24 Hours
Heating & Air Conditioning in Joshua
Since 2003, Comfort Masters Heating & Air Conditioning has been working tirelessly to help the people of Joshua achieve their perfect definition of comfort. Our team of certified technicians is dedicated, passionate, and make strong working relationships with our clients. We make it our mission to bring unparalleled service to ensure that our clients are taken care of. This involves open and honest communication, ongoing training for our staff, and keeping up to date with the latest innovations in the HVAC world. It is no wonder that more and more people are putting their trust in Comfort Masters.
Services We Offer to the City of Joshua
Air Conditioning Repair
Coming home to a hot house after a long day at work is absolutely miserable. It can leave you and your family feeling uncomfortable and irritable. Knowing you have a team that can quickly respond when your air conditioner needs immediate repairs and provides long-lasting solutions is paramount to your family’s comfort and well-being. Contact our team today for more information on our air conditioning repair services for both our commercial and residential clients in the Joshua area.
Gas Furnace Installation
Gas furnaces are a fantastic heat source during the cold and bitter winter months. Keeping your family comfortable and well-cared for is our number one concern, which is why we offer quick and reliable gas furnace installation services.
Air ducts are the transportation center for your home’s conditioned air. When there is a leak in your system, then your air may be taking an unwanted detour, leaving particular rooms in your home feeling uncomfortable. Thankfully, your dedicated team at Comfort Masters Heating & Air Conditioning can help you put your air ducts back into working order.
Resources in Joshua, Texas
Comfort Masters Heating & Air Conditioning is proud to serve the people of Joshua and the surrounding areas, such as Burleson. Contact our team today for more information on our services or to schedule an appointment!
for Joshua, TX
Sandra - Joshua, TX
Judy and Jason Murphy
Jason - Joshua, TX
Geno did a great job and didn’t mind my husband watching him and learning. He arrived around 10 this morning and finished around 8 tonight. Very pleased.
Sandra - Joshua, TX
Very helpful and efficient. They call and let you know when they will arrive and if they are running behind they will let you know.
Great service and fast response time.
Lucretia - Joshua, TX
12-07-2020, Arrived on site to perform a fall maintenance on three gas systems, Verified all major components functioning normal and had to replace one capacitor. I did find out that they were having some issues with voltage irregularities. Discussed options of installing surge protectors and we went ahead and installed them. No issues with the systems and they are ready for fall. 0CO readings, gas lines are tight, flue pipes are secure. Returned all thermostats back to normal. Thank you for giving us the opportunity to serve you.
System had a failed compressor. Installing new 5-ton heat pump.
6-01-2020, Found both condenser coil and evaporator coal have a leak in it. Customer approved replacing parts of warranty coil’s. Drove to Garland to pick up both coils and return to install. Installed new coils and filter line drier. Pressurized system with nitrogen to verify no leaks. Pulled vacuum and charge system with 10.5 pounds of 410a Freon. System has two new pistons. Checked and verified 20.5° temperature split across the coil with 8° superheat and 15° sub cool. Condenser fan motor and compressor functioning properly, blower motor functioning properly, System is now ready for summer. Thank you
5-08-2020, Arrived on site to perform 83 system maintenance and replace filters. Found master bedroom unit 1 pound low on Freon. Added 1 pound of r410 a Freon. Verify drain lines are clear, temperature split on all three units are 20° split, sprayed down evaporator coil‘s, washed outdoor coils, all systems are functioning properly and ready for summer. Thank you
Signed up customer with a 3 system quarterly maintenance
PLease let us know how we did