Best A/C and Heating Services in Keller
Keller residents and business owners need to have a steady supply of cool air during summer and heated air during winter in order to stay comfortable. That’s why it pays to call on Comfort Masters for service when you have a central air conditioning system or a heating system that breaks down on you. It doesn’t matter what kind of HVAC system you have at your home or business; we have a team of HVAC experts available to provide you with service for central A/C systems, heat pumps, furnaces, and much more.
When you count on Comfort Masters for your heating and cooling needs, you’ll get service that is affordable, prompt, and of the highest quality. Our professional HVAC team provides the best A/C and heating services in the Keller area, including routine maintenance, installations, and repairs.
A/C and Heating Unit Installation and Repair in Keller
Although HVAC systems are made to last for many years, yours isn’t going to last forever. Whether you need emergency repairs at odd hours or need to look into having your system replaced, you can count on Comfort Masters for expert help. Our licensed HVAC professionals can repair your system or recommend having a new one installed, depending on what best suits your situation. We can also schedule regular maintenance once a year to help your HVAC system last longer and run better.
At times, you might need to have HVAC equipment replaced, such as when yours is heavily damaged or worn down from years of use. Our technicians offer replacement services for residential and commercial HVAC systems in Keller when you run into this problem. No matter what your HVAC needs are, you can rely on our professionals for outstanding service.
Comfort Masters’ Commitment to Great Customer Service
Our experts at Comfort Masters understand how crucial it is to have an HVAC company that you can truly depend on, whether you need sudden repairs or routine maintenance. Since 2003, our company has been ensuring that residential and commercial property owners in Keller get outstanding service for any HVAC work they need. Managers Stephen P. Moore and Jesse I. Roberts oversee a team of highly skilled technicians who can provide prompt HVAC service.
Customers who have turned to us in the past have left glowing reviews online, so that others can see how dedicated we are to exceptional service. These reviews frequently mention the punctuality and dependability of our technicians, and our customers have been very grateful that they can rely on us to get their HVAC system working again quickly – even in the middle of summer. We are a proud winner of Angie’s List’s Superior Service Award of 2017, and we have been given an A+ rating from the BBB, as well as accreditation.
Living in Keller
Keller offers residents a high standard of living thanks to incomes that are higher than average, as well as spacious, upscale homes. Those who live here have a median household income of $122,292, which is considerably higher than the Texas median household income of $54,727 and the national median household income of $55,322. Residents pay an average of $311,700 for a house in Keller, compared to an average home price of $142,700 in Texas and $184,700 in the U.S.
Roughly 47,266 people call Keller home, and the city has steadily increased its population over the years. Those who live in Keller only have to drive about 18 miles via TX-121 S to get to Fort Worth, and Dallas is just 32 miles away via TX-114 E. This makes it convenient for Keller residents who commute and those who want to enjoy all that the larger cities have to offer.
From local parks to special events, Keller has its own amenities and attractions for residents. Those who love to play golf can set up a tee time at Sky Creek Ranch Golf Club. Bear Creek Park offers hiking trails, playgrounds, a wildscape garden with a waterfall, and scenic views of the creek and pond. Families can keep the kids entertained at Johnson Road Park, which features an Imagination Station playground, as well as a sandbox and picnic tables. Residents can enjoy music and meals at Bronson Rock, or dine on a platter of barbecued pork at Spring Creek Barbeque. The city also hosts several community events throughout the year, such as night hikes and holiday festivities.
Keller residents who want to put their skills and talents to use can volunteer to help local organizations, such as Keller Public Library or Animal Services. The city also has several Boards and Commissions available that residents can serve on, including the Crime Control and Prevention District Board, Planning and Zoning Commission, Public Arts Board, and Economic Development Board.
Have questions about the HVAC services we provide for residential and commercial customers in the Keller area? Contact Comfort Masters Heating & Air Conditioning, and we’ll give you more details on our HVAC services, including repairs, maintenance, and installation. We can also schedule service for your HVAC system if you’re ready to get prompt repair services.
for Keller, TX
Chase - Keller, TX
Payne and Boatner DDS - Keller, TX
Karol - Keller, TX
Professional Informative Precise Great group of people the whole team is the best !
David - Keller, TX
Great service all around.
Christian - Keller, TX
David - Keller, TX
Bobby was professional and thorough
Great service. Chase conley
Chase - Keller, TX
Shane - Keller, TX
They came out when nobody else could
Ronald - Keller, TX
I was in desperate need of AC help, fighting problems all week with another company that showed up twice, wouldn’t return my calls and I still had problems. Really liked the technician. Give him a raise.
Came out to perform prepaid maintenance on clients 2 Trane systems, upon arrival performed maintenance by checking motors, voltages, amperages, drain lines, float switches, cleaned filters, delta t’s, capacitors, contactors, refrigerant charges, washed out outdoor units with water hose, etc., etc.. please see maintenance checklist for details, systems are operating well within manufacturer specifications.
Came out for recall no cool on upstairs, upon arrival turned on system in the cool mode and system came right on and began cooling. Was not able to get it Reenact the issues, but whenever I changed out the contactors I was wondering why would I have to change both contactors at the same time and then when it started up on whatever day I was out here last I did hear the contactor chatter I spent some time to try to figure out why the contactors are chattering but it would not show itself, the only thing that I can for see it being is the control board that has a relay that is. chattering and won’t completely sit in the call for cool, Explain to the client that this is basically a shot in the dark, but is an educated shot in the dark and since the they have family coming out they want to the system up and running well by the time they get here so I’m going to go ahead and order a control board as well as the communicating tcont900 thermostat due to the fact that the client was telling me
Came out for upstairs unit is not cooling, upon arrival started checklist by checking motors, voltages amperages, delta t, etc., etc.. found that the outdoor unit was not running due to circuit 1 compressor contactor was not sending voltage thru on common circuit, having office checking for warranty and ordering part once we have them will have Tricia in the office call to schedule replacement of contactor. 6/9/2020 came out to change out the y2 contactor, replaced contactor, started up system in the cool mode, System came on everything and cooling in second stage, allowed system to run for a few minutes and found that system was a little low of 410 a refrigerant. Added 3 pounds for 10 a refrigerant with client approval system is now operating at 9° sub cooling and 22° superheat in high stage. Put system in test mode operation for first stage, And found the contactor two was not pulling all the way in to allow voltage to go through it, replaced it as well. Tested stage one cooling agai
Came out due to water leaking from mini split system in closet, upon arrival checked overhead mini split by checking filters, delta t, washing out outdoor unit with water hose, clearing out drain line with vacuum (see pictures due to drain line is a little hard to find). System is operating well within manufacturer specifications with a 20° delta T with the return air at 70° in the supply air at 50°.
Came out to perform Quality Check as well as install OEM low ambient control kit on clients brand new Trane 2 stage air conditioning with Gas furnace , upon arrival performed QC by checking wiring, motors, seal of system, over all cleanliness of install, Delta T which is at 18°, with the return air temperature at 65° and the supply air temperature at 47°, check charge ( picture can be found in history), surge protectors, air purification system, etc. etc.. Then went ahead and installed low ambient control kit per the book, left book with services facts in the outdoor unit with a label saying it was in there, also left stricter on the outside unit explaining that due to low ambient kit outdoor fan motor will click in and out depending on outdoor temperature. System is operating well within manufacturer specifications.
Came out to perform prepaid AC maintenance on clients 2-4 yr old Lennox systems as well as install Reme Halo whole house air purification system, upon arrival performed maintenances by checking wiring, voltages, amperages, filters, drain lines, delta t’s, refrigerant charges, capacitors, contactors, washed out both outdoor units with water hose, etc., etc.. systems are operating per manufacturer specifications. Installed Reme Halo to downstairs system by cutting hole in supply plenum, and then wiring it to its own transformer and wiring that transformer direct to high voltage coming into system. Filled out warranty registration card and gave to client so he could register Reme Halo for its warranty.
Came out due to both clients systems were having issues, upon arrival found that the upstairs system 824 thermostat was stuck in a white screen, performed reboot and system came on and began cooling at 20° delta T. This system is still under its two year labor warranty and there will be no charge for it. Upon arrival to down stairs unit found that system only had a 5° delta T and that the system was low of R22 refrigerant, added 5 lbs of R22 system is now operating at 15° sub cooling and 11° superheat. client waived option to have me perform a leak search but would like to have Don come out and educate client on upgrading system to 410a refrigerant.
4-28-2020, today I arrived on site to perform a two system one time spring special. I found downstairs evaporator coil has leak. Performed digital leak search and found leak in the coil. Also found outdoor condenser fan motor making a winding, ringing loud sound while running. Also found it low on Freon. Advised homeownerDue to the age of the system it is best to invest in replacing the unit. Upstairs unit is performing OK at this time. Emergency drain pan recommended replacing due to rust. Thanks
Came out for prepaid ac maintenance on clients 2 1yr old Trane systems, upon arrival performed maintenances by checking motors, capacitors, wiring, electrical connections, delta T, filters, amperages, voltages, refrigerant charges, washed out both condensers, etc., etc.. systems are operating well within manufacturer spec at this time, and everything looks great.
Came out to perform heat maintenance on client 2 Trane furnaces, upon arrival performed heat maintenance by checking motors, wiring, electrical connections, voltages, amperages, check ductwork for leaks, capacitors, temperature rises, etc., etc.. found that systems are operating well, but the downstairs system has a lot of air leakage at start collars. Client was close so I brought him in and showed him. Also noticed that client does not have any air sanitization, informed clients on products that we offer on air sanitization. Sealed up duct work at plenum, added Reme halo to supply side plenum, filled out warranty registration card for client.
Came out to replace uv air purification bulbs on both of clients systems, replaced both bulbs and then tested to ensure proper operation, both are operating according to manufacturer spec. Also check filters in systems for client while in the attic, both look good.
Came out to replace uv bulbs on both systems, replaced both bulbs and tested to ensure proper operation. Both are working according to manufacturer spec. Also checked filters for client while in the attic and both look good.
Came out today for Quality Check/ Heat Maintenance on clients 2 brand new Trane systems, upon arrival perform QCs by thoroughly checking thru install, checking wiring and setting of equipment, making sure install is nice and clean, making sure that the duct work is hung properly. Performed fall maintenance by making sure that everything heat looks good and is working properly. Install looks GREAT, and systems are operating GREAT as well.
Came out for a funny smell when client tried to turn in the heat mode, upon arrival started up furnace in the heat mode and was not able to get smell to return, however while checking over system found that clients existing flu/vent pipe was rusted and falling apart. With client approval returned with new flu/vent pipe and replaced it (due to the dangers of carbon monoxide) now furnace is venting properly and safely.
Compressor is shorted on 20 year old Trane split system