Contact Comfort Masters Heating & Air Conditioning in North Richland Hills, TX
Open 24 Hours
Heating & Air Conditioning in North Richland Hills
Since 2003, Comfort Masters Heating & Air Conditioning has been helping the people of North Richland Hills achieve the perfect temperature in their homes. Our expert technicians are certified and highly-qualified to solve any issue that your HVAC unit may have. We serve both residential and commercial clients by providing unparalleled repair, replacement, and new installation services. We ensure that our clients’ HVAC units are up-to-date and that our repairs and installations are built to last.
Services We Offer to the City of North Richland Hills
Air Conditioning Maintenance Services
Wear and tear over time can shorten your air conditioner’s lifespan and leave your home feeling uncomfortably hot during the summer. Routine maintenance is the best way to protect your air conditioning unit to ensure that it lasts for years. Comfort Masters Heating & Air Conditioning can perform A/C tune-ups, air conditioning unit cleanings, and routine maintenance checks to make sure your air conditioner stays in top shape.
Residential Air Handler Repairs and Installations
Residential air handlers are responsible for ensuring that you have good airflow through your ducts and vents. When this equipment fails to work properly, your home can become uncomfortable for you and your family. Our residential air handler repair and installation specialists will help you keep your air handler up and running all year long.
Air Duct Services
Air ducts allow air from your HVAC system to travel to the different parts of your home. Regardless of whether you are heating or cooling your home, the air won’t travel very far if your air ducts are experiencing issues. Comfort Masters Heating & Air Conditioning will help keep your air ducts in working order!
Comfort Masters is proud to serve the hard-working people of North Richland Hills, TX and the surrounding areas, including Colleyville, Keller, and Grapevine. We combine excellent customer service, reliability, and dedication to give our customers the service they deserve. Contact our team to get an estimate today!
for North Richland Hills, TX
Shane - North Richland Hills, TX
Overall great experience and did exactly what they said they would. Followed through very well.
Gail - North Richland Hills, TX
Janis - North Richland Hills, TX
Very nice people to work with.
Sandy - North Richland Hills, TX
A technician came out the same day I called. When I decided to replace the entire system the technician made sure someone came out that same day to present my options and that installation could occur the next day. I was given 4 options in my price range. System was installed the next day. A week later another technician came out to review installation. Everyone I dealt witn was efficient, professional, courteous and respectful of me and my property-all this during a pandemic. I was very impressed with the service I received.
Gail - North Richland Hills, TX
Great Tech, Great Service
Elizabeth - North Richland Hills, TX
Spent time with me to make sure I understood all aspects of my system, and future work we discussed.
Great service, awesome price
Justin - North Richland Hills, TX
James was awesome and very knowledgable. He fixed my AC issue the first time and the price was fair
David - North Richland Hills, TX
Mike did a fine job inspecting my a c system. He was thorough but did not try to oversell me on unnecessary services.
Came out due to system is going out in low pressure, after investigation found that zone 1 damper was stuck in the closed position, was able to force it open and then remove wires so that zone would be open for moving air until we could order and then replace zone damper motor. Returned and replaced zone 1 damper motor and then tested operation of both zone dampers. Zoning system and ac is operating per manufacturer specifications.
Initially came out due to hot and cold spots in home, initial assessment was that client needed manual dampers and a bigger return air on unit to allow for proper and then adjustments to air flow in home. Came out performed the job, and today came out because client says it’s a lot better but that one of the rooms were staying 2 degrees warmer, performed adjustment with dampers and then recalled space with client, definite improvement in the air coming to that room.
Came out to perform AC maintenance on clients less than 2 yr old Trane heat pump system, upon arrival performed maintenance by checking motors, wiring, amperages, voltages, capacitors, filter, delta t, refrigerant charge, washed out outdoor unit with water hose, etc.., etc.. replaced 20x20x4 filter and left remaining 2 at unit. System is operating per manufacturer spec. Bought back Clearsky Dm w/ discount on air scrubber air purification.
6-09-2020, Arrived on site to identify why the system is not functioning properly. Found 4° temperature split across the coil. Checked and verified with digital leak detector that there is a leak in the evaporator coil. System is an R22 system. Found blower wheel with extreme debris reducing airflow, 15 µF capacitor reading 11 µF, outdoor door capacitor reading 54/4 µF of 50/5 µF. System is going into negative vapor saturation. 19 psi on the low side with 93° superheat. Discuss prices of repairs versus the system being 25 years old it is best recommended to replace the equipment. Customer has an appointment set for today with Don. Thank you
5-21-2020, We installed a new complete A/C system, 5-29-2020, Today I arrived on site to perform a quality check on the new system installed. Verified zone control board functioning properly, both thermostats functioning properly, zone motor dampers functioning properly, drain lines are clear, 20° temperature split across the coil, new 16X25X4” Merv 11 filter installed, Took several pictures of the installation. Great job guys! Also installed an air scrubber purification air system. Check the outdoor unit to verify everything is functioning properly. System is functioning as per manufacture specs. Thank you
Came out to due to water all over the floor, upon arrival found a clogged drain line, performed drain line clear out and was able to get drain line draining again. Went through performing service checklist on clients 31yr old system by checking motors, wiring, voltages, amperages, capacitors, contactor, delta T, charge of system, filter, etc., etc.. please see service checklist for details. After performing service checklist came to client and let them know the recommendations for repairs on system, right now client has chosen to go with a floor saving float switch to prevent water on the floor from a clogged drain line. Also client would like to have Don come out and educate them on upgrading system to the 410a refrigerant as well as educating them on what higher seer rated systems can do for them. If client does chose to upgrade system all of today’s repairs come with the new system and today’s ticket will need to be discounted from the install of new equipment.
Came out to perform heat maintenance on clients less than 2 yr old Trane heat pump system, upon arrival performed maintenance by checking electrical heat, motors, wiring, amperages, voltages, capacitors, heat pump heat heat, etc.., etc.. replaced 20x20x4 filter and left remaining three at unit. System is operating per manufacturer spec. Added Clear Sky Ion Generator air purification to system.
Came out today to perform heat maintenance on clients Trane heat pump system, as well as give an estimate to run new duct from start collar to grille in pantry. Upon arrival perform heat maintenance by checking motors, heat strips, amperages, voltages, electrical connections, filter, wash out the outdoor unit, etc. etc. system is operating per manufacturer spec. Was able to work up est. for client in regards to running ductwork.
Fixed stuck dampers