Contact Comfort Masters Heating & Air Conditioning
Hours of Operation:
Open 24 Hours
Heating & Air Conditioning in Saginaw, Texas
Since 2003, Comfort Masters Heating & Air Conditioning has been providing unparalleled heating and cooling services to both residential and commercial clients in Saginaw, Texas. Our team has allowed Saginaw to find its perfect definition of comfort with high-quality HVAC repairs, maintenance, and installation services. The HVAC technicians on our team are all certified to help solve even the toughest HVAC problem, allowing you to enjoy life no matter the temperature. When it comes to reliability, there is no other team like Comfort Masters!
Services We Offer to the City of Saginaw
Air Conditioning Repair Services
Nothing is worse than your air conditioning giving out on you in the middle of the summer. The team at Comfort Master can help you get your air conditioning back up and running! We offer timely repair services so that you and your family can come home to total comfort instead of a hot house. From drainage issues to refrigerant leaks, rest assured that our team will quickly find the issue and take the proper steps to ensure that it gets resolved.
Air Handler Services
Your air handler is responsible for ensuring that you have good airflow through your ducts and vents. When this equipment begins to break down, your home can be left feeling uncomfortable. The dedicated HVAC technicians at Comfort Masters Heating & Air Conditioning can repair your air handler and return comfort to your home! Keep your home feeling comfortable and contact our team for your air handler repair services today!
Commercial Heating and Cooling Services
When your business’s HVAC system isn’t working properly, it can leave your employees and customers feeling uncomfortable. This leads to lower sales, unhappy customers and employees, and lower productivity. Don’t let a faulty HVAC system cause your business to suffer and instead, turn to the reliable team at Comfort Masters. With our Commercial HVAC repair and installation services, we can ensure that your business is always feeling comfortable no matter what time of year it is. Improve productivity and keep your customers and employees happy and put your trust in Comfort Masters today!
Local Resources for Saginaw, Texas
Comfort Masters Heating & Air Conditioning happily serves the people of Saginaw, Texas, and the neighboring cities, including Watauga, Haslet, and River Oaks. Contact our team today for all of your heating and cooling needs!
for Saginaw, TX
Integrity & Trust
TAMAggies - Saginaw, TX
Whenever Geno is on-site I’m confident he will find the real problem and not just swap parts. Very happy with their service!
On Time, Wore Mask
Elaine - Saginaw, TX
Bobby was great.
Polite, Knowledgeable service, amazing price!
Bobby - Saginaw, TX
Bobby Aderholt was absolutely amazing, he came to assess our situation and was polite and respectful. He gave us the step by step on our issue and sold us on the platinum package so they can keep up with our service. He quoted up step by step on the pricing and started with our concerns!!! He was the absolute best!
Chris - Saginaw, TX
Bobby came out and did a QC on our new HVAC system. He was polite and very knowledgeable. I would definitely recommend!
Claudia - Saginaw, TX
Excellent. Very prompt and friendly. Very good service thank you
12-08-2020, Performed fall maintenance on one of their rental properties. Found temperature rise reading low so I increased the gas pressure to achieve a higher temperature rise so the house would heat Up quicker. Check the rest of the system and found all major components functioning normal, safeties are working, gas line is tight, flue pipe is secure, unit is sealed properly. No issues at this time. Thank you for giving us the opportunity to serve you.
Performed system maintenance on a Amana heat pump
Came out due to high humidity in home, upon arrival spoke with client to find out in her own words what was going on, after discussion performed service checklist by checking motors, voltages, amperages, drain line, filter, delta t, capacitors, contactor, refrigerant charge, condenser coil cleanliness, etc., etc.. while performing checklist found that dual capacitor for outdoor unit was reading 43/4.4 of 50/7.5, this is well below manufacturer specifications and was recommended to replace, also found that the condenser coil was pretty dirty, spoke with client about moving system to maintenance and client approved, washed out condenser coil thoroughly with water hose, as of today the only thing that I was able to find that would contribute to high humidity in home would be the dirty condenser coil. System is operating per manufacturer specifications. Spoke with client about our maintenance membership programs and client has chosen to decline at this time.
Came out due to 2 bedrooms not keeping up in the heat of the day, upon arrival performed checklist by checking duct work, motors, voltages, amperages, drain lines, float switch, delta t, capacitors, contactor, condenser coil cleanliness. While performing checklist found that system was double filtered, one in the filter grille and one up at the unit, took filter out of filter grille and let client know what happens when it is double filtered like that, also found that the 2 rooms in question normally left their doors closed, let client know that with the doors closed there is no way for the system to circulate the ambient heat out of the room therefore without air circulation those rooms would not be able to cool. Also found that 9” duct that feeds those 2 rooms is at the beginning of the plenum so if by removing that one filter and keeping those doors open during the day that we would need to move into adding manual dampers into the system and then performing an air balance to force m
Came out to perform Quality Check on clients brand new 18 seer 2 stage heat pump system, upon arrival performed quality check by checking motors, voltages, amperages, wiring, electrical connections, delta t, refrigerant charge, breakers, seal of equipment, overall cleanliness of install, etc., etc.. while performing QC found that the TXV did need to be adjusted, adjusted TXV to the proper charge. System is now operating at 9.5° sub cooling and 14.8° superheat with a delta T of 19° with the return air temperature at 71° in the supply air temperature at 52°. System is operating per manufacturers specifications.
Came out for a warranty no cool, upon arrival turned the system on in the cool mode, upon arrival found that unit started right up and began cooling, upon arrival to air handler found that the float switch though not engaged has water in it, used a pitcher of water to fill up primary drain line and the primary drain line was clogged, tried to perform drain line clear out with pressurized nitrogen down and into sink with 75 psi of nitrogen, than tried with 100 psi and was not able to clear drain line, took a trash bag and taped it over primary drain line at air handler, then went to sink where it drains to, cut drain line and blew it back to trash back and felt zero resistance, pulled apart p trap u dear sink and found that the Tee under sink was completely clogged, took it completely apart and washed out Tee and 3/4 primary drain line that hooked to Tee with water hose and then took towel and clean off pipe from sink that slide down into Tee, added bleach to primary drain line to clean
J Replace ends on compressor common wire. Install hard start kit. Replace contactor. 1 year part and labor warranty on repairs.
Working on the Air Conditioning