Hours of Operation:
Open 24 Hours
Heating & Air Conditioning Services in Watauga, Texas
Comfort Masters Heating & Air Conditioning has been helping the people of Watauga with all of their heating and cooling needs since 2003. Our team of experienced and exceptional HVAC technicians work diligently to ensure that our clients’ homes are always at their perfect temperature! We use the latest in air conditioning and heating technology, ensuring that your home’s HVAC system is up-to-date and any repairs or replacements are built to last.
Services We Offer to the City of Watauga
Even though Texas is not known for its particularly frigid winters, it can still get cold. Comfort Masters can help you keep your family warm and comfortable all winter long with heater inspections, repairs, and replacement services! Don’t suffer in the cold; contact your trusted team at Comfort Masters today!
Air Conditioning Services
Having reliable air conditioning during the scorching summer months of Texas is essential for maintaining the health and comfort of your family. This is why Comfort Masters Heating & Air Conditioning team is readily available to solve any problems your A/C unit may face! Whether you need repairs, a refrigerant recharge, or a replacement unit, our team can help!
Comfort Masters doesn’t just serve our residential clients in Watauga but we also provide unbeatable and timely services to our commercial clients! Our team can help get your business back to its perfect temperature allowing your team and customers to keep moving forward.
Local Resources and Events in Watauga
- Watauga’s Community Events
- Halloween Bash
- October of every year (dates may vary)
- Halloween Bash
- Watauga 4th of July Celebration
- July 4th of every year
- Veteran’s Breakfast and Celebration
- November of every year (dates may vary)
- Watauga’s Hometown Christmas Celebration
- December of every year (dates may vary)
Comfort Masters Heating & Air Conditioning is proud to serve the people of Watauga, Texas, and the surrounding areas, including Colleyville, Keller, North Richland Hill, and Bedford. Don’t settle for less than the perfect temperature; contact our team today!
for Watauga, TX
Honest tech, great service
Mark - Watauga, TX
Tech came out to check system, confirmed my hypothesis on problem. Pointed out other things for me to repair/replace to improve system. Loved getting honest answers to my questions, even if I ended up just paying the call-out fee and replacing parts myself.
Lonnie - Watauga, TX
I had a problem with the AC. Called my usual AC company. They wouldn’t come out and told me that it was a plumbing problem. I talked to a few friends and they highly recommended Comfort Masters. Comfort Masters showed up same day I called and took care of my problem. Plus found and fixed other problems with my unit that the other company did not find or even check for when they were out a week ago. Thank you Geno!
Paulette - Watauga, TX
Used these guys for a new install and for maintenance. Always timely, great service and reasonable fees. Would definitely recommend to friends and family!
Kirk - Watauga, TX
Mike was great, he Talked to you every step of the way as to what he was doing and how he was going to do it.Great sense of humor.Mike is great with customer service.
8-05-2020, Met with Mark and we went to the outdoor unit. Checked and verified the motor bearings are going out. The motor will come on but start squealing and vibrating. Recommend replacing the condenser motor along with dual capacitor. 50/7.5 µF capacitor is reading out of range. Checked the rest of the system and found the evaporator coil has animal for building up on the coil and filter does not fit properly in the filter rack. Also the platform is bowing and causing the system to sink slightly into the platform. System is in the closet. Customer is aware that system needs to be replaced but he’s not prepared at this time to replace the equipment. Also discuss pricing of the condenser motor with Mark and he mentioned that he is going to perform the repairs on his own. Thank you
Came out to perform quality check on clients brand new Amana system, upon arrival spoke with client about how the system was treating them, client expressed concern that the new unit seems to be a lot louder coming out of the vents, to address this concern slowed the fan speed from 420cfm per ton down to 350 cfm per ton. This did allow for a quieter supply grill in the living room, still a little louder in the bedrooms made a suggestion of instead of using throw grilles that maybe a three way stamp face would be a little quieter due to a lot less static pressure at grille, client stated that he would try that, other wise may want to snake a couple of the ducts around a little bit so that they are not coming directly off the plenum. Client does not like the idea of using manual dampers because they don’t want to cut airflow. Then proceeded with QC by checking wiring, electrical connections, overall seal and cleanliness of job, delta t, and refrigerant charge. System is operating per man
6-18-2020, right on site to try and identify why Was there water on the floor. Found that Lonnie had already cleared the drain lines in install drain pan tablets. I use the label to verify that the system is flat. Notice the evaporator coal has lots of rest. Check the bottom side of the Evaporator coil and did not see any debris. Checked pressures on the outdoor unit and found system low on Freon. After I got approval I added the appropriate amount of Freon to increase the sub cool from 1.6 to 7° sub cool, 20.8° superheat with 131.8 suction pressure and 350 liquid pressure. All capacitors motors and compressor is working normal. Customer has had bad experience with other companies that has services equipment. Also found that the post which was not functioning at all. Removed float switch from the circuit and customer is not ready to replace at this time. Washed outdoor unit. Sign customer up with standard maintenance plan. Return system back to normal use. Thank you
Came out for a prepaid maintenance on clients 2 yr old Trane system, upon arrival performed maintenance by putting system into test mode (cooling stage 2) and then checking motors, voltages, amperages, capacitors, contactor, delta T, washed out the outdoor unit with water hose, etc., etc.. system is operating per manufacturer specifications, please see maintenance checklist for details.
Fixed condensation line that was tripping float switch. Redesign line by venting after trap.