Contact Comfort Masters Heating & Air Conditioning in Benbrook, TX
Open 24 Hours
Heating & Air Conditioning in Benbrook
Comfort Masters Heating & Air Conditioning has been helping the people of Benbrook maintain the perfect temperature in their homes since 2003. Our team of dedicated, passionate, and highly-qualified technicians works tirelessly and efficiently to ensure that every household in Benbrook maintains the right temperature all year long. We provide new installations, inspections, and repairs. With ongoing training, a focus on communication between our team and our clients, and a dedication to keeping up to date with the newest innovations, it’s no wonder more and more people turn to Comfort Masters for help.
Services We Offer to the City of Benbrook
Electric Central Heating Repairs
When your electric furnace is on the fritz, it can leave your home feeling icy cold. The Comfort Masters team of professionally trained HVAC technicians can help you solve your electric heater’s malfunctions. We never want to leave our clients shivering in the cold which is why we don’t quit until the problem is solved. If you have an electric heater that is in need of repairs or you are looking to install a new one, contact us today!
Air Conditioning Maintenance
Your air conditioning works hard to ensure that your house remains cool all summer long. You can increase the lifespan of your unit by investing in routine maintenance checks. Our team at Comfort Masters Heating & Air Conditioning is more than happy to take a look at your unit and take the necessary steps to prevent a breakdown during the hottest months of the year.
Commercial Heating & Air Conditioning
Texas is known for its hot summers and random bouts of nasty cold weather in the winter, so when it comes to ensuring your business is at the right temperature, you can trust our team. Comfort Masters Heating & Air Conditioning has been helping commercial properties reach and maintain their optimal temperature for years! Give us a call today to take back control of the temperature of your building.
Comfort Masters Heating & Air Conditioning is proud to serve the people of Benbrook and the surrounding areas, including Aledo, White Settlement, and Westworth Village. Contact us today for more information on our services!
for Benbrook, TX
Patricia - Benbrook, TX
Very patient and kind service technician
pleased with the service
Judy - Benbrook, TX
Came the same day we called and was polite and took care of our needs.
Birdwell - Benbrook, TX
Stephen did a great job. He came out quickly after we called and fixed our issue. Great service and affordable price.
Excellent Replacement of Old Systems
Lynn and Chris - Benbrook, TX
Our home had older R-22 1.5 an 3 ton A/C systems. They were replaced with Amana 2 and 3 ton heat pumps. Since their installation, they have been used in both heating and cooling modes.Comfort Masters left the installation area in the attic very clean. They vacuumed the area in the attic at the end of each day. Old equipment was removed as requested. The outside installation was clean and equipment installation looks clean and orderly.The new controls are easy to program and adjust. The systems are both two stage and operate at two different levels depending on how much cooling or heating is required. The system automatically chooses the level.I think the new systems are a big step up compared to the previously installed systems. Overall, I’m extremely happy with the new equipment and Comfort Masters personnel both pre-sale and installation.
Louis - Benbrook, TX
bobby was great, professional, and thorough.
Louis - Benbrook, TX
On time, friendly, and house is cooling!
Leslie - Benbrook, TX
James was an exceptional technician. Checked our new AC/ heating system for hot spots, showed me how to get logged into the WiFi and gave a tutorial on how to access features on the new thermostat. Very savvy and friendly
Dee - Benbrook, TX
Had a leak in unit. Trisha worked extra hard to get me fit in, she is a real treasure. James showed up on time, identified problem and got it fixed. This is my second time using them, and both have been very positive customer service experiences. Definitely recommend.
7-07-2020, signed up Miss Patricia for a silver club maintenance plan. I was able to unclog her drain line and clear it. Also install drain pan tablets to help prevent future clogs. Recommend this once a year during the summer. Filter size is 20 x 25 x 4 and needs to be replaced Patricia ordered some online and they are coming soon. Temperature split across the coil is 20°, superheat is 23°, subcool is 8°, inside temperature was 90°. Found that thermostat was not properly communicating with the Wi-Fi. We reset the Wi-Fi and thermostat is now communicating. Washed outdoor condenser. System is now ready for summer. I did mention search protectors and air quality. Customer is not interested at this time. Thank you
Performed to system one time spring maintenance. Found both systems low on Freon. Homeowner approved adding Freon. Added 3 pounds of Freon between both units. Noticed both filters are 20X25X5 inch Merv 16 filter’s And need to be replaced. Customer says they replace them once a year. Customer is trying to locate filters to be replaced. We do offer replacing both filters for $191.23 plus $89 service call. Both systems are now functioning properly with 20° temperature split across the coil and all pressures and temperatures are correct. Washed both outdoor units. Returned both systems back to normal use. Thank you
18 year old system a little low on r-22. Added and system is working great!!!
Came out to to give estimate on moving unit and then gave estimate on moving unit and adding/enlarging return air on both systems
Came out to perform quality check on clients brand new 16 sear two-stage heat pump system, upon arrival performed QC buy checking wiring, seal, delta T, charge and overall cleanliness of job, etc., etc.. Found system to be operating with a 21° delta T, and system to be operating at 13° sub cooling and 13° superheat. System is operating well within manufacture specifications. Pictures of data plates are in history.
Came out to pull and clean evaporator coil as well as replace condenser fan motor, upon arrival pumped system down and then pulled evaporator coil, then took it outside and cleaned it, reinstalled coil, replaced used o-ring on TXV, pulled vacuum on system down to 600 microns, replaced condenser fan motor, started up system in the cool mode, added 410a refrigerant, system is now operating at 8° sub cooling and has a delta T of 21°. System is operating per manufacturers specifications.
Came out to perform ac maintenance on clients 10 yr old system, upon arrival performed maintenance by checking motors, voltages, amperages, capacitors, delta t, filter, cleanliness of cabinet and evap coil, contactor, charge, etc., etc.. while performing maintenance found that the evaporator coil was dirty and needed to be pulled and cleaned and that the condenser fan motor bearings were locked up and not allowing the fan motor to operate, have called and ordered part, and scheduled replacement of fan motor and the pull and clean of evap coil for tomorrow between 2-6pm.
Initially came out for no heat on heat pump system. Came out to find refrigerant flow restricted at outdoor TXV need to replace TXV. 11/20/2019- upon arrival pump refrigerant forward into line set an evaporate coil, pulled faulty txv, replaced it, pulled vacuum to 530 microns, replaced burnt contactor started up system in cool mode, added 3 lbs 410a system is operating per manufacturer spec.