Contact Comfort Masters Heating & Air Conditioning in Benbrook, TX
Open 24 Hours
Heating & Air Conditioning in Benbrook
Comfort Masters Heating & Air Conditioning has been helping the people of Benbrook maintain the perfect temperature in their homes since 2003. Our team of dedicated, passionate, and highly-qualified technicians works tirelessly and efficiently to ensure that every household in Benbrook maintains the right temperature all year long. We provide new installations, inspections, and repairs. With ongoing training, a focus on communication between our team and our clients, and a dedication to keeping up to date with the newest innovations, it’s no wonder more and more people turn to Comfort Masters for help.
Services We Offer to the City of Benbrook
Electric Central Heating Repairs
When your electric furnace is on the fritz, it can leave your home feeling icy cold. The Comfort Masters team of professionally trained HVAC technicians can help you solve your electric heater’s malfunctions. We never want to leave our clients shivering in the cold which is why we don’t quit until the problem is solved. If you have an electric heater that is in need of repairs or you are looking to install a new one, contact us today!
Air Conditioning Maintenance
Your air conditioning works hard to ensure that your house remains cool all summer long. You can increase the lifespan of your unit by investing in routine maintenance checks. Our team at Comfort Masters Heating & Air Conditioning is more than happy to take a look at your unit and take the necessary steps to prevent a breakdown during the hottest months of the year.
Commercial Heating & Air Conditioning
Texas is known for its hot summers and random bouts of nasty cold weather in the winter, so when it comes to ensuring your business is at the right temperature, you can trust our team. Comfort Masters Heating & Air Conditioning has been helping commercial properties reach and maintain their optimal temperature for years! Give us a call today to take back control of the temperature of your building.
Comfort Masters Heating & Air Conditioning is proud to serve the people of Benbrook and the surrounding areas, including Aledo, White Settlement, and Westworth Village. Contact us today for more information on our services!
for Benbrook, TX
Joseph - Benbrook, TX
Brenda - Benbrook, TX
Service was great, tech was courteous and professional
Josie - Benbrook, TX
Great Service and timely response.
Crystal - Benbrook, TX
Always very knowledgeable, explains everything
Patricia - Benbrook, TX
Very patient and kind service technician
pleased with the service
Judy - Benbrook, TX
Came the same day we called and was polite and took care of our needs.
Birdwell - Benbrook, TX
Stephen did a great job. He came out quickly after we called and fixed our issue. Great service and affordable price.
Excellent Replacement of Old Systems
Lynn and Chris - Benbrook, TX
Our home had older R-22 1.5 an 3 ton A/C systems. They were replaced with Amana 2 and 3 ton heat pumps. Since their installation, they have been used in both heating and cooling modes.Comfort Masters left the installation area in the attic very clean. They vacuumed the area in the attic at the end of each day. Old equipment was removed as requested. The outside installation was clean and equipment installation looks clean and orderly.The new controls are easy to program and adjust. The systems are both two stage and operate at two different levels depending on how much cooling or heating is required. The system automatically chooses the level.I think the new systems are a big step up compared to the previously installed systems. Overall, I’m extremely happy with the new equipment and Comfort Masters personnel both pre-sale and installation.
Louis - Benbrook, TX
bobby was great, professional, and thorough.
Louis - Benbrook, TX
On time, friendly, and house is cooling!
Inspected system on no heat
12-10-2020, performed pre-paid, fall maintenance on one Trane, 2 stage, gas furnace. Head to increase gas pressure to increase temperature rise. Temperature rise is now 40°. Advise Mr. Reed he needs to replace his 20 x 25 x 4“ Honeywell filter. Also had to re-calibrate the screen on his 1050 thermostat. He has mentioned he’s had several outages in his neighborhood. I discussed with him about search protectors and he says he has a home search protector. Verbal speed motor at 5.5 A, IDM motor at .8 A, cleaned flame sensor and reading at 2.5 µA, All safeties functioning properly, 0CO readings, gas lines are tight, flue pipe is secure, system is sealed properly, drain line appears to be clear. No further issues recorded at this time. Return system back to normal use. Thank you for giving us the opportunity to serve you
12-09-2020, performed the fall maintenance owed from new install. Signed up Michaela with our silver club maintenance plan. Verified all components functioning properly in heat pump mode and electric heat. Replaced customer provided filter and found dual capacitor was failing but covered under warranty. Went ahead and replaced it and verified no other issues. System is now ready for fall. Thank you for giving us the opportunity to serve you
Checked electric heat air handler
Performed maintenance on new heating systems hp Amana
Float switch tripped
9-12-2020, upon arrival the thermostat was off but the outdoor system was still running and the evaporator coil was frozen. Check the outdoor unit and found that the contactor head welded shut causing the outdoor unit to stay on. Talk to customer about our club membership and she declined at this time. Advised her that her parts are out of warranty. She Approved repairs and I replaced the contactor. Tested system operation and system is functioning OK at this time. System does have a 19.5° temperature split across the coil with blower motor at 3.5 A, pressures are, suction pressure 121 psi, liquid pressure 272 psi, such in temperature 54°, liquid temperature 82°, superheat 12°, sub cool 8°. Advise customer if they burn candles that they should replace the filter more frequently. Wax and suet buildup on the filter. There is a hole behind the thermostat that is giving false readings on temperature. Advise customer they need to sell up the hole. I did shove some insulation inside but they
Came out to perform AC maintenance on clients system for home client just purchased, performed maintenance by checking motors, voltages, amperages, filter, duct work, drain line, float switch, delta t, capacitor, contactor, refrigerant charge, washed out outdoor unit with water hose, etc., etc.. while performing checklist found that system is operating within manufacturer specifications but that the compressor is showing signs of laboring and weakening due to its RLA are 16, and compressor is operating at 15.3A, also let client client know that the outdoor unit is not a heat pump and operates off of the old R22 refrigerant, please see checklist for details.
Came out to perform maintenance, upon arrival spoke with client about our maintenance membership programs, and client has chosen to go with our silver maintenance membership. Performed maintenance by checking motors, voltages, amperages, drain line, float switch, filter, delta t, capacitor, contactor, refrigerant charge, washed out outdoor unit with water hose, etc., etc.. while performing checklist client showed me where the drain line for the unit was dripping under the sink, while investigating that found that the brass fitting was loose, tightened with wrench, and drain line stopped leaking, drain line is free of clogs. System is operating per manufacturer specifications, please see checklist for details. Spoke with client about our Air scrubber air purification system by Aerus, and client has decided to go ahead and have one installed into their system. Installed air purification system into the supply plenum of clients HVAC equipment.
7-07-2020, signed up Miss Patricia for a silver club maintenance plan. I was able to unclog her drain line and clear it. Also install drain pan tablets to help prevent future clogs. Recommend this once a year during the summer. Filter size is 20 x 25 x 4 and needs to be replaced Patricia ordered some online and they are coming soon. Temperature split across the coil is 20°, superheat is 23°, subcool is 8°, inside temperature was 90°. Found that thermostat was not properly communicating with the Wi-Fi. We reset the Wi-Fi and thermostat is now communicating. Washed outdoor condenser. System is now ready for summer. I did mention search protectors and air quality. Customer is not interested at this time. Thank you